In kitchens, all outlets that serve countertop surfaces should be equipped with GFCI outlet protection. That would include any outlets on walls, behind wet areas (sinks, etc.) that have features such as countertop breakfast bars (open counter surfaces above sinks used to sit at on the opposite side).
How many GFCI outlets are required in a kitchen?
one GFCI You only need one GFCI if its installed as the first outlet in the circuit and wired properly. Every outlet in the kitchen was required to be protected by GFCI.
Do all kitchen outlets need to be GFCI?
All countertop receptacle outlets must be protected by a GFCI device installed at the outlet or by GFCI circuit breakers. A kitchen must have two 20-amp circuits for countertop appliances. There should be countertop receptacles installed so that no point along the counter is more than 2 ft. from an outlet.
Do you only need one GFCI per circuit?
A GFCI is not dependent of a ground to function. The GFCI circuit breaker controls an entire circuit, and is installed as a replacement for a circuit breaker on your homes main circuit board. Rather than install multiple GFCI outlets, one GFCI circuit breaker can protect the entire circuit.
Which outlets on a kitchen countertop need to be GFCI protected?
All 125-volt, single-phase, 15- and 20-ampere receptacles installed to serve the countertop surfaces in kitchens must be GFCI protected.
Where should a GFCI be placed in a kitchen?
Kitchens: All receptacles serving countertop areas and any receptacle within 6 feet of a sink must have GFCI protection. Also, the receptacle supplying a dishwasher should be GFCI-protected.
How far does an outlet have to be from a kitchen sink?
Kitchen Outlets This applies even if there isnt a nearby sink, such as on a bar or island. Additionally, no point on the wall should be farther than 24 inches from an outlet in either direction (meaning 4 feet total between outlets), so you must have an outlet within 2 feet of the kitchen sink.
Are 20 amp outlets required in kitchen?
Kitchens need to be on a dedicated 20-amp circuit and require 12-gauge wire. Today, 12-gauge wire is wrapped in a yellow sheath, but your old cable may be white. New circuits in kitchens need both arc fault and ground fault circuit interruption (AFCI, GFCI) protection.
Should a refrigerator be on a 20 amp circuit?
You should have refrigerators and freezers installed on a 15-20 amp dedicated 120 volt circuit. This will avoid an electrical overload due to your current wiring not being capable of handling the additional power.
Can you have a plug socket under a sink?
5 Answers from MyBuilder Electricians Take it you mean fit a socket in the cupboard below the sink? - yes this is permissible but the socket should be accessible and mounted so its unlikely to get water drips on it should the waste or other pipe below the sink leak.